SUCTION RECIRCULATION 17-11
A line is connected between the suction of the pump and the bottom of the stuffing box or seal gland connection. Many pumps have a connection already tapped at the suction throat of the pump for a suction gage, but if none is available you can install one in the piping or a pipe flange if the piping is not thick enough to be drilled and tapped. Try to make the stuffing box connection as close to the seal faces as possible to insure a good circulation through the stuffing box.
Stuffing box pressure is almost always higher than the suction pressure of the pump. Liquid from behind the impeller will be circulated through the stuffing box to the pump suction. The impeller has centrifuged this liquid and the result is that the liquid going into the stuffing box is considerably cleaner than what you are pumping. In many cases you can eliminate the need for bringing in clean liquid and diluting your product.
This environment control works very well in closed impeller pump designs and those open impeller designs that adjust towards the pump volute rather than the back plate such as most Flowserve (Duriron) pumps.
You should not use suction recirculation in the following applications:
For information about my CD with over 600 Seal & Pump Subjects explained, click here
Link to Mc Nally home page