REVERSED IMPELLER R013
Some double suction impellers can be mounted in reverse, or backwards on the shaft. If the impeller is reversed, several things can happen:
- The pump’s capacity and efficiency will be reduced.
- Power consumption will increase. This could overload and damage the motor.
- The discharge head will stay about the same.